Figure 7-7.Equipment housing ground connections (line side).
Figure 7-8.Equipment housing ground connections (load side).
Although this rule of the Code prohibits neutral
cord or run with the circuit conductors. The conductors
bonding on the load side of the service, sections
may be bare or insulated. The insulated conductors
250-50(a) and 250-53(b) clearly require such bonding
must have a continuous outer finish of green or green
at the service entrance.
with one or more yellow stripes.
The circuit conductors used for equipment
When the equipment grounding is to be
grounding must be within the same raceway, cable, or
accomplished by the protective device of the circuit