Figure 2-1.Bath unit, portable, major components.
drawn back into the water source. If this arrangement is
not possible, dig a ditch or build a dike around the
shower stands to allow wastewater to drain away from
the water source. When a pressurized water source is
used, discharge the water into an open reservoir before
it is drawninto the bath system. This prevents excessive
strain on the water pump. Use the following procedures
to set up the bath unit:
Do not connect the heater to an untested
water supply. Contaminated water can cause
illness or death.
To prevent equipment damage, be sure the
hose couplings are free of dirt or foreign matter
and the coupling gaskets are in place before
you couple the hoses.
1. Connect the section hose strainer to the male end
of a 25-foot long, l-inch ID hose.
2. Connect the female end of the water hose to the
water pump suction port.