grooving operation. In all cases, the inside diameter of the duct is the determining factor for board size. To determine board size see table 13-4.
To form a rectangular duct, the flat duct board is measured accurately and grooves are cut at the proper locations. The board is then folded into a rectangular shape. When the board is cut, an overlapping tab is left and this is then pulled tight and stapled. Tape is applied and the joint is heat sealed. Joints between sections are made by pulling the shiplap end sections together.
The joint is then completed by stapling, taping, and heat sealing the junction as shown in figure 13-3.
Sheet metal ducts expand as they become hot and contract as they become cold. The degree to which expansion and contraction becomes an installation factor depends upon the temperature of the air surrounding the ducts and the temperature of the air moving through the ducts. Fabric joints are often used to absorb this duct movement. Additionally, fan noise and furnace or air-conditioner noise tends to travel along the
Table 13-4. - Duct Board Length Selection ChartContinue Reading